Products
Rewards
from HOLOOLY

We are determined to provide the latest solutions related to all subjects FREE of charge!

Please sign up to our reward program to support us in return and take advantage of the incredible listed offers.

Enjoy Limited offers, deals & Discounts by signing up to Holooly Rewards Program

HOLOOLY
BUSINESS MANAGER

Advertise your business, and reach millions of students around the world.

HOLOOLY
TABLES

All the data tables that you may search for.

HOLOOLY
ARABIA

For Arabic Users, find a teacher/tutor in your City or country in the Middle East.

HOLOOLY
TEXTBOOKS

Find the Source, Textbook, Solution Manual that you are looking for in 1 click.

HOLOOLY
HELP DESK

Need Help? We got you covered.

## Q. 11.4

A compressed air system has a mechanical power requirement of 50 kW with a motor efficiency of 90 percent. Determine the cost savings of reducing the discharge absolute pressure from 800 kPa to 700 kPa. Assume that:
• The compressor is operating 4,000 hours per year with an average load factor of 70 percent.
• The cost of electricity is $0.05/kWh. ## Step-by-Step ## Report Solution ## Verified Solution Assuming that the intake air pressure of the compressor is equal to 100 kPa (i.e., 1 atm), the reduction in the discharge pressure corresponds to a reduction in the pressure ratio $P_{o}/P_{i}$ from 8 to 7. The percent reduction in the mechanical power requirement $\%W_{m}$ can be calculated using either Eq.(11.3) or Eq.(11.4): For an isothermal compression: $\dot{W}_{m}=\dot{m}_{a}.R_{a}.T_{i}.Ln(\frac {P_{o}}{P_{i}})$ (11.3) $\dot{W}_{m}=\frac {\dot{m}_{a}.R_{a}.T_{i}.γ}{γ-1}[(\frac {P_{o}}{P_{i}})^{\frac {γ-1}{γ}} -1]$ (11.4) $\%W_{m}=\frac {LN(8)-LN(7)}{LN(8)}=6.4\%$ Using Eq. (11.8), the electrical energy savings can be calculated: $ΔkWh_{comp}=\frac {\dot{W}_{m}.LF_{comp}.N_{h,comp}.(T_{i,e}-T_{i,r})}{η_{M}.T_{i,e}}$ (11.8) $ΔkWh_{comp}=\frac {0.064*50kW*4000hrs/yr*0.70}{0.90}=9950k Wh/yr$ Thus, the cost savings due to a reduction in the discharge air pressure are about$500/yr. For an adiabatic compression:

$\%W_{m}=\frac {(8)^{1.4-1/1.4}-(7)^{1.4-1/1.4}}{(8)^{1.4-1/1.4}}=5.7\%$

Using Eq. (11.8), the electrical energy savings can be calculated:

$ΔkWh_{comp}=\frac {0.057*50kW*4000hrs/yr*0.70}{0.90}=8870k Wh/yr$

Thus, the cost savings for reducing the discharge air pressure are about \$450/yr.